Post By: Anonymous (not verified)
Posted Date: Thu, 2019-05-16 13:29
Hi, I am working in ESBR wastewater treatment plant. We are struggling with a issue of Low MLSS, MLVSS in aeration tank and high COD after secondry clarifier.
- MLSS-700 PPM, MLVSS- 300 PPM
- Inlet COD 700-800 PPM and after secondry clarifier it is upto 400 ppm.
So, please suggest how to increase our MLSS/MLVSS and reduce COD in our plant.